That chart is for when the indoor conditions are within human comfort conditions. It assumes RH is 55% or lower. Not that the indoor conditions are 85°F DB 76°F WB/66.6%RH.
If your system was working in a 100°F ambient, at those readings. You would probably find your SH and SC within 5° of each other. If the indoor was at human comfort conditions.