1. Professional Member
Join Date
Oct 2008
Posts
507
Post Likes

## Trying to calculate latent load from pool evaporation. help?

I've got a therapy pool at 15x12ft. =180sqft
They want to maintain the pool at 90F and the air temp at 85.F.

I'm trying to determine the latent load my unit will see just from the pool evaporation portion of the space load.

I think its Delta grains x4.5 x CFM = lb/hr then I need to convert that to BTU/hr.

I think I'm missing how to get the grains and how to get to BTUs.
I've done this before but its been a while.

Any help appreciated.

2. Here is a worksheet that helps figure the moisture load from a pool at the different conditions you find with applications.
http://www.thermastor.com/Pool-And-S...a-Brochure.pdf
This save a lot of time to dicuss the possibilities.
Regards TB

3. Professional Member
Join Date
Oct 2008
Posts
507
Post Likes
In case anyone stumbles across this thread looking for the same thing, here is what I found.

The calculation is Latent load (kbtu/hr)= 0.1 * surface area (sqft) * differential vapor pressure * Activity factor.

0.1 is a constant.
Differential pressure comes from Steam tables of saturated air. In my case I have 90 degree water and 85 degree air. The tables show that 85 degree air at 50% RH has a vapor pressure of about 0.68.
The vapor pressure of 90 degree air at saturation is about 1.42
1.42-0.72=0.7 in this case.
I realize I used the 90degree saturated air vapor pressure. This is because right at the surface of the water, the particules of water are trying to go into the atmosphere and the pressure of the air is resisting that. Nonetheless, those air particles right at the surface are fully saturated. Thats why differential pressure is key here.

Activity factor is a value based on the type of water body it is. A therapy pool or hot tub has an activity factor of 1.0.
A swimming pool has an activity factor of 0.5
A wave pool has a 1.5 factor.
This pool is 15ftx12ft

In my case this resulted in the following 0.1*.7*180*1= 12.6 MBH =12,600 btus of latent heat.

I also think that when a latent btu is created, a sensible btu is absorbed so I think that the overall btu load remains constant but I wasn't sure how to factor that in. I left my space load as was and just added another 13,000 btus of latent for the system to have to handle.

4. Regular Guest
Join Date
Jun 2004
Posts
30
Post Likes
This is the Ask Our Pro's forum. In order to post a response here, you must have verified qualifications and have been approved by the AOP Committee. You may ask a question by starting a new thread.

You can find the rules for posting and qualifications here.

Additional infractions may result in loss of posting privileges.
Last edited by jpsmith1cm; 07-13-2013 at 07:13 PM.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.