split system - r22 with fixed meetering device carrier condenser and goodman gas furnace 100k btu. This is an old unit in one of the our fire stations. pre inspection, after unit was thawed showed clean filter - we change them out quarterly, clean indoor and outdoor coils, airflow good on both coils, voltage and amps good. Low side was 40 psi and high 190 but due to quickly freezing up I din't have a chance to check the superheat and subcooling. I recovered the refrigerant, nitro pressure tested it with no leaks. Although they looked clean, I cleaned both coils, orfice for the fixed meetering device (screen look debris free) and replaced the filter drier. Pressure tested again all good. evuacated the system and charged the system. Had a hard time getting all 7lbs back in the system. Suct pressure was good 65-70 psi, super heat 12 subcooling in the 40s Discharge was 290 and raising quick. vsp was 45deg and lst was 110 deg. Any ideas would be much appreciated.