Customer had/has a leaking evap - would not replace a month ago.
Customer had a compressor fail - would not replace evap now.
I installed an R407 condenser and a huge LL drier
This is the result:
Outdoor Ambient 82º
Indoor Ambient 82º
Head press 180 lbs = bubble point 85º
Suction press 75 lbs - dew point 38º
LL temp 72
Subcooling = 13º
Suc temp 66
SSH = 28º
Evap air TD - 82º-65º = 17º
How does it look to you?