BACnet Loop point in JCI NAE
I have a BACnet/IP fcu controller of distech controls and i want to integrate it in an JCI NAE. The problem is that the setpoint point is a loop point (i saw it with a distech controls tool) and from auto discovery of the NAE this point is not discovered. How can i insert this point, in the manual insert point wizard i do not have this option for inserting a loop point.
Thanks in advance
From another post a long time ago it was determined that some NAE do not support BACnet control loops. From the PICS here: http://www.bacnetinternational.net/, it appears that it is the MS-NAE85xx-xx series. Not sure about the Distech product line, with s
ome more info you can check it's PICS, but most lines support BACnet control loops.
"Open is as open does."
- Forrest Gump
"Can't we all just get a Lon?"
- Garry Jack
"BACnet: integration or interrogation?"
- The Janitor
"Open protocols? You can't handle open protocols!"
- Nathan R. Jessup
“What’s that? Aaa… open protocols? Don’t talk about…. open protocols? Are you kidding me? Open protocols? I just hope we can hardwire an interface!”
- Jim Mora http://www.youtube.com/watch?v=U7fjDS0jKiE