Well, Robo here is another quality control update.
AHS -no heat
New Goodman horizontal furnace/new system 0405 serial
Get there and find low voltage fuse blown, so start checking and find shorted thermostat wires, so check out system and find also motor had high amp readings , check returns , filter and capacitor OH MY. 20uf 370 capacitor installed from factory as customer have only lived there since August 2005 and have only had regular maintenace performed I ask if any motor repairs had been made. None. Called American Distributors FTW andf ask what cap goes on the 1/2hp motor , just to make sure no changes had been made at Goodman I wasn't aware of nope, 10uf 370 . So I guess that if amp draw is 10.9 motor has seen a loss because of quality control. Trouble is now who pays,AHS or customer for motor, under warranty..
Up date to follow: Well, looks like AHS won't cover because it was factory defect, so customer will be paying for labor and parts aquistion..
Motor 9.6 with 20 uf 370
Motor 10.9 with 10uf 370