Hello and thank you for reading my post.
I'm kinda new to the commercial side of hvac and I'm having a problem with one of my units. I know I'm forgetful some times and forgot the SC and SH. heat pump comp 1 the line from the accumulator to comp is cold . but going into it is warm. the cap tubes are cold but the coil it self is warm. reversing valve suction side is warm. I have tested the reversing valve and it's working as far as i can tell. So my thoughts on this could be the cap tubes or the liquid line going into the cap tubes might be clogged. Any help is appreciated