1. Regular Guest
Join Date
May 2005
Posts
404
Post Likes

## Sizing a Humidifier/Dehumidifier

How do you size a humidifier? Once RH is determined for the conditioned space, can find grains of moisture from psych chart...then what?

How about a dehumidifier? The opposite?

Thanks!

2. Regular Guest
Join Date
Jan 2007
Posts
11
Post Likes

## Sizing

3. Regular Guest
Join Date
Jan 2007
Posts
40
Post Likes

## Dehumidifier

I THINK A 6FT CRAWL SPACE HAS ABOUT 3X THE VO LUME OF A 2FT CRAWL

4. Professional Member
Join Date
Aug 2004
Location
Dupont Pennsylvania
Posts
327
Post Likes
I'm also interested in any info, I have a place with about 150 tons of air I have to Quote humidification in.

5. Regular Guest
Join Date
Mar 2007
Posts
1
Post Likes

## Humidification and dehumidification

Use the equation

m=4.5(scfm)(w2-w1)

Where:

m= moisture removed or added (lbs)
w=humidity ratio (from psych. chart lb of moisture/ lb of dry air)

6. Volume of the space does not work. You need the air change rate on the space and the moisture generated in the space. Humidification or dehumidification is based on the amount of air change, the moisture content of the make-up, and the desired moisture level in the space. Example assuming no space load:
150 cfm of 70^F dew point, 110 grain make-up air
75^F, 50%RH, 56^F dew point, 66 grains
(150 cfm/14 cf/Lb) * (110 grains-66 grains)/lb air * 60 min/hr =28,285 grains of moistue/hr
28,285 grains/7000 grains/lb=4 lbs of moisture per hour removed or added= 4,200 btus latent.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.