either another bad valve ...or something restricting the gas flow..... inlet pressure fine ...outlet low..... usually the valve......
it was working.... played with it.... now its broke.... whats the going hourly rate for HVAC repair
yup, inlet stays at 6.6" the whole time
Is there a regulator in the line that could be acting up?
Officially, Down for the count
YOU HAVE TO GET OFF YOUR ASS TO GET ON YOUR FEET
It was working when I left...
Liberalism-Ideas so good they mandate them
Is this the customers only unit?
Anything else on their meter?
does voltage to the valve stay constant
Only unit on that meter, no regulator up stream, voltage stay constant.
Talked to Lennox tech support and after a lot of talking, he thinks i have an inducer issue.
I'm heading back there tomorrow morning, i'll post any updates.
I would check the burner orifice for an obstruction, if the manifold pressure is fluctuating this much there has to be some sort of blockage in the burner. I am assuming you replaced the gas valve.
And you are certain that there is a steady pressure coming to the unit from the meter, right?
Originally Posted by Slim_Miller
[Avatar photo from a Florida training accident. Everyone walked away.]
2 Tim 3:16-17
RSES CMS, HVAC Electrical Specialist
AOP Forum Rules:
You nailed it.
Originally Posted by Betabass
Orifice was partly blocked. It was burning fine but was making my vacuum in the burner box fluctuate, making my manifold pressure go crazy. Everything is great now.
Thanks everyone for your ideas
Normally, when you have a partially blocked orifice, the flame will appear different than the other burner flames. Do you recall seeing any difference in the flame?