Results 1 to 4 of 4
02-10-2013, 03:43 PM #1Regular Guest
- Join Date
- Feb 2007
American Standard 2 Stage Heating Air Handler HELP! ??
I hope I am posting this in the right area of the forum. If not Admin please reasign. I have a number (24) AS convertible air handlers that has a secondary electrical heat source. The original owner of the building had the electircal side disconnected because of the cost of the electric. I am having a hard time figuring out how to reconnect it. White wires 2 + 3 on the molex plug have been disconnected but I cant figure from where. I believe it is looking for 24 volts to energize the 220 relay for the heater..
PLEASE HELP! ..
02-10-2013, 04:27 PM #2Professional Member*
- Join Date
- Oct 2009
- Raleigh, NC
You aren't going to get DIY help for that here, sorry! And, it looks to me like your diagram shows where white wires 2+3 on the molex plug terminate!
02-10-2013, 06:14 PM #3
Look at the wiring diagram for the actual heat package.If more government is the answer, then it's a really stupid question.
02-19-2013, 12:52 AM #4
This is the Ask Our Pro's forum. In order to post a response here, you must have verified qualifications and have been approved by the AOP Committee. You may ask a question by starting a new thread.
You can find the rules for posting and qualifications here.
Additional infractions may result in loss of posting privileges.
Last edited by jpsmith1cm; 02-19-2013 at 05:56 AM.