Define when the coil would be considered wet enough to test...
Originally Posted by chill67
Dry is dry. Wetness can vary. That's why York doesn't publish wet coil airflow data.
when does detaT calculate in initial starting or after stabilizing?can use this formula in 3phase and single phase fan?
Originally Posted by mason