Results 1 to 13 of 14
02-09-2013, 07:39 PM #14
It seems to be getting in from all the knockouts and around the inspection access doors. I have been sealing every hole with foil tape i can find in the trouble units i run into. Once i do this and put thicker gasket material on the top of the door it seems to be helping. The last one i had tripped the unit breaker and the 200 amp panel breaker. there was a 4"diameter hole on the control board.