cant see how this passed an inspection
found these on a roof the other day.
first one is of a rtu exhausting into the MUA intake.
I wasnt aware of the add-on kit for the concentric kit.
best part is all this work passed city inspections.
would never pass here...... inspector would rupture his appendix laughing
it was working.... played with it.... now its broke.... whats the going hourly rate for HVAC repair
The first is MUA? Is it an industrial location and they just don't care?
on that concentric they directed the flue gas to be pulled back in as combustion air.
how does anyone think that is close to correct?
The Food Stamp Program, administered by the U.S. Department of Agriculture, is proud to be distributing the greatest amount of free meals and stamps EVER.
Meanwhile, the National Park Service, administered by the U.S. Department of the Interior, asks us to "Please Do Not Feed the Animals". Their stated reason for this policy "... the animals become dependent on handouts and will not learn to take care of themselves."
from an excerpt by Paul Jacob in Sun City, AZ
It would pass here because the inspector wouldn't have any idea what he was looking at, much less that it may be wrong.
If more government is the answer, then it's a really stupid question.
I have to admit, they tried hard screw up that concentric.
I had to "extend" just the end of a concentric once. Was a pain in the butt to find something that would fit it,
"Better tell the sandman to stay away, because we're gonna be workin on this one all night."
"Dude, you need more than 2 wires to a condenser to run a 2 stage heatpump."
"Just get it done son."
What's up with that 4" pipe cap on it's side?