replaced a compressor #1 on a goodman package unit. M#PCB120-3. Unit has txv. After starting and running for 20 min i was getting these readings. comp#1 rla 18.6, 13.1, 13.4 , 14.3. Blwr rla 8.4, 6.2, 6.0, 5.7. CF rla 3.5 , #1,3.0,#2,2.8. pressures 52/160. S.L. temp 31. sh 3. L.L. temp 87. sc 0. amb 70. ra 73. sa 54. return air grill is clean, as is evap, blowr wheel, and cond. Motor pulley has been changed and is maxed out. im thinking txv stuck open., but wouldnt i have a higher suction pressure. txv bulb is attached properly to line. ran out of time store closed will return to finish tommorow. what do you guys think.