Results 1 to 5 of 5
01-31-2013, 05:11 PM #1
Integrating Some TAC/Invensys Actuators
01-31-2013, 05:25 PM #2
Here a datasheet 3v operating range anywhere between 2-15
Kevin"Profit is not the legitimate purpose of business. The legitimate purpose of business is to provide a product or service that people need and do it so well that it's profitable."
01-31-2013, 05:40 PM #3
Thanks for the info.
So do I understand this right......the range is 3vdc. The starting point(approximate) is 6vdc.....but is fixed. But also states, that the starting point is adjustable. And requires 2-15vdc.
Now I'm even more confused.
02-01-2013, 04:29 PM #4
02-01-2013, 05:44 PM #5
I threw a commissioning tool on a valve today. It does only seem to stroke between about 6-9vdc.
I also monitored the existing controllers that are controlling the Ahu's. They were feeding 4vdc at 0% and 9vdc at 100%. The system is a old Tracer 100.
So I'm just going to set up my new controllers at 6-9vdc.