I have tandem 300 ton 19xrv's using a atmospheric tank serving two different processes. both chillers are set for 40F LCWT with hotgass set at 44 with a 2F diff. One process batch loads and the other goes into high temp alarm at 47F. I know that the chillers aren't designed for batch loading but when the batch process heats up there's no way the chillers can load fast enough to compensate for for the load before the other process goes into high alarm. One of the chillers stays in hotgas until the LCWT reaches 48F even wt the hotgas controller set at 44 wt 2F diff. My thinking is, if i can get the chiller out of hotgas quicker it might help the pull down response. Any ideas how to find a happy median?