My system is a 2.5 ton York Affinity air-air heat pump with electric strips.
At our airflow speed setting, which is the lowest possible, we have a noticable difference in air speed between heating with the heat pump only and when all the heat strips are engaged.
I would like to minimize this difference.
Provided the heat strips allow it, if I were to ask our contractor to install a TTSCC01 communicating thermostat, would that thermostat allow us to select something like 1000 CFM for cooling AND for electric heating (presently it's set at 1086 cooling, 1248 heating)?
The jumpers don't allow more flexibility.
I know you cannot do that with a furnace, but maybe with my system?