Results 1 to 3 of 3
Thread: (ending the day with ice in FL)
01-28-2013, 08:19 PM #1Regular Guest
- Join Date
- Sep 2012
- cape coral FL
(ending the day with ice in FL)
One of are accounts calusa pines golf club. exclusive golf club 260 members 36 pro's in Naples FL. If you like golfing Google it, its a sweet place. I get there at 4:00 today to look at there kitchen unit. It's about a 10 ton package unit with 2 compressors. I shut off the unit and look in to see my comp's full of ice. I look in at my cooling coil and just the bottom half iced up about 5-6in. I think to myself that is a different ice pattern. My outdoor temp is 77 and last night temp was 58. Blower has new pulleys and new belt running at 60% of it's RLA. I do not think its a r22 prob knowing the charge was good about 25days ago. Coil is in good shape with nice clean filters. If its an airflow prob its electrical. I don't know if the set point at night is to low and running all night. It being a kitchen it might be hot at night calling for cool and the outdoor temp being 58 could make it an ice machine!!! I unplugged the comp's and opened the fresh air and will be back tom.
01-28-2013, 09:38 PM #2Professional Member*
- Join Date
- Oct 2004
- toledo, ohio
You never have a flat tire ...... Until you do ...
01-28-2013, 11:06 PM #3