Results 1 to 6 of 6
Thread: Which disconnect?
01-28-2013, 09:24 PM #1
01-29-2013, 12:22 PM #2Regular Guest
- Join Date
- Oct 2004
Your attachments don't open.
01-29-2013, 12:29 PM #3
Somebody decided to run some extra stuff off of that baby. Be careful crawlin around the attic you never know what crazy loose connections are in there.Certified parts changer.
01-29-2013, 08:20 PM #4
whats goen on here? looks like one add on is 240. is this condenser disconect? I saw one lasty week end "add on" in some ones basment switch was nailed to ceiling been with no box and electrical tape wrapped around the terminals going to two lights wired in series last light box had a hot wire cut off just hanging thier about 4 inches out. I think the tried to wire more in series and it didnt work so they cut the excess off.
01-30-2013, 11:36 AM #5Professional Member*
- Join Date
- Jul 2000
- Northern Wisconsin
The safest disconnect means for that building might just be to go outside and pull the meter.Use the biggest hammer you like, pounding a square peg into a round hole does not equal a proper fit.
01-30-2013, 01:55 PM #6
It was a rental. I sent pictures and a letter via certified mail saying they need to fix it.
Sent from my SCH-I510 using Tapatalk 2