Originally Posted by crmont
A bad txv at the outside unit can cause high head pressure just like he's seeing & still work fine in cooling. We haven't been given any SH, SC or even suction pressure measurements so that leaves a few possibilities besides just air flow until we get them.
An engineer designs what he would never work on.
A technician works on what he would never design.