Results 1 to 6 of 6
01-22-2013, 09:38 AM #1
Trane univent discharge air sensor location
We have over 100 trane univents that they used an averaging sensor for the discharge air. The coil is about 4 inches below the sensor and the bypass is behind the coil so when we bypass the coil we still get alot of heat on the sensor so we get a lot of complaints about blowing cold air since the unit thinks it is blowing warmer air.
Anyone seen this before? Any sugestion on how to fix it?
Sorry I hope you understand what I am talking about. Thanks