Victory VF-1 stand up reach in single stainless door freezer
Compressor is AFE13C3E-IAA-901 copeland
complaint , wont hold temp , imagine that
200 high , 5 low , 50 deg inside box ( no product ) , pullin 12 amps
Feel drier , its warm incoming , and cold right where the cap tubes are brazed into the stub. I knew then its got to be clogged. Normally they are warm a couples inches up cap tube before they get cold.
Cut it out , then cut it open , sure enough the dessicant beads had busted through the screen and clogged it up.
Install new drier , amazingly caps still looked good , I could blow through both caps just fine , braze back in.
Both coils clean
Pull her down , Weigh in 10 OZ 404
Fire it up , I have 210 high , 28 low , pulling 9.2 amps , evap frosting evenly
10 min later the evap fan comes on , starts falling from 50 degrees to 45
210 high , 25 low 9 amps , cant measure Sh Sc , cant find my dam clamp on
Few minutes later for no reason ..... compressor shuts down.
Few minutes later hear "click" hmmmmmmm Click
Throw infared thermometer on shell , reads 145 deg , seems normal , but whatever , Get out ice , cool it down.
Runs again 10 minutes , evap frosting nicely , fan kicks on
Few min later compr shuts down.
Before I beat it with a hammer , I pack up and go home.
Why would it shut down when everything is going so well ??