Problem: heat pump produce no heat, only blow cold air.
Insight: Called for heat, Blower ran, but compressor didn't come on.
Cause: dirty air filter cause the high pressure switch to trip during heat mode.
Solution: While it was calling for heat, checked 24v on the Y wire from the thermostat at the unit, got 24v. checked 24v at the compressor contactor coil, no voltage. found High pressure swith is in between, reset it. cleaned the air filter, turned the heat back on.
Sorry guys, after a few posts and I saw some reply and they looks like spams. So I thought u guys are just machines, and that's why I stop posting. Hahahah
If you get 15 posts you can apply for pro membership and do as in depth and technical walkthroughs as you want in the locked pro forums, you also might find out some things even you didn't know.... : )