Results 1 to 4 of 4
Thread: Mitsubishi multi error code?
01-15-2013, 07:19 AM #1
Mitsubishi multi error code?
I'm going to look at a multi system and the customer told my dispatcher their t-stat is giving a error code of "k"? I haven't had a chance to look into mitsi's mylink site for their troubleshooting guide. Wanted to throw it out there for anyone to chime in. TIA FitzChaos equals cash$$$
01-16-2013, 05:19 PM #2
Found error code 6607-No ACK. It is a Communication error. Traced a few wires and found a communication wire cut due to recent renovations and the carpenters no knowing they accidently sliced it or just not mentioning it...Chaos equals cash$$$
01-16-2013, 05:23 PM #3
Easy find?Local 597 Service Fitter
Metal Trade Journeyman
PAY ME NOW OR PAY ME LATER
It was working when I left...
01-16-2013, 05:58 PM #4
16ft ceilings with 2 cassettes running off 1 stat. There was also a lonnassy unit tied into this meeting room. I just happen to look at some wires zip tied to the spiral duct and noticed one lying on the ceiling tile. I found the other end and said to myself this was done deliberately or accidentally. Was the first citi multi I've worked on since I took the course months ago. Spent the day their checking wiring and addresses. Some good on the job trainingChaos equals cash$$$