Results 1 to 4 of 4
01-10-2013, 08:23 PM #1
TRANE YCH180 IGNITION BOARD FAILURE CODES
Would any one have the codes for the flashing led on the ignition board. No info on the unit 2004 install.
Roof top nat gas . Went to trane site, no help. Getting four green flashes"My hands are for sale"
01-10-2013, 08:36 PM #2
Does the Unit have Reliatel Controls? Is it a Texas Instuments board? If so then it is a high limit fault.Gotta have the right tool for the job!
Where is all the stuff MADE IN THE USA?
"Thats what we do Troy. Incredible, Invisible, Imbelivable things. We are an Unseen, Unknown, Unvincible fraternity of craftsman.."
01-10-2013, 09:16 PM #3
Thank you P 10. I was just checking some othe manuals I have for a 2004 unit. Both limits in series. If either breaks gives you a "4" flash of the green LED.
Thanks for you time! Mr HVAC"My hands are for sale"
01-10-2013, 10:16 PM #4