Results 1 to 13 of 18
Thread: What's missing??
12-28-2012, 05:43 PM #1
Had a no heat call, this is what I find.
12-28-2012, 05:47 PM #2
Did the home owner remove the pressure switch? I can't believe a tech would do that."The bitterness of poor quality remains long after the sweetness of low price is forgotten". --Benjamin Franklin
"Don't argue with an idiot, they will drag you down to their level and beat you with experience". --Mark Twain
"Beer is living proof that God loves us and wants us to be happy" --Benjamin Franklin
12-28-2012, 05:54 PM #3
Home owner did it, said it's ran fine like that for awhile. Couldn't get through to him how unsafe it is. Knew everything.
12-28-2012, 05:59 PM #4
Ahh, the old jerry rigged trailer unit.
Sad. Just sad."Better tell the sandman to stay away, because we're gonna be workin on this one all night."
"Dude, you need more than 2 wires to a condenser to run a 2 stage heatpump."
"Just get it done son."
12-28-2012, 06:10 PM #5
You nailed it hvacvegas.
12-28-2012, 06:12 PM #6
Missed an opportunity to thin the herd.
12-28-2012, 06:59 PM #7
wow ...that is just plain wrong....it was working.... played with it.... now its broke.... whats the going hourly rate for HVAC repair
12-28-2012, 07:10 PM #8
Dude I have not laughed like that in a while! Thanks for the laugh.....thin the herd...
12-28-2012, 07:38 PM #9
Those trailer units always have something special in store for you
12-28-2012, 08:27 PM #10
12-28-2012, 08:45 PM #11
How does this even work? Doesn't the logic in most systems check to see that pressure switches are open at the beginning a cycle and then closed after at some point after the inducer is energized???
12-28-2012, 09:29 PM #12Professional Member*
- Join Date
- Jun 2011
- Muncie, Indiana
12-28-2012, 09:57 PM #13
If I'm remembering correctly this unit has an ignition box that only cares about flame signal and closed safeties, if it's getting the 24v to the box it's good, so let the removal and jumping out begin!