Results 92 to 104 of 168
01-01-2013, 03:01 PM #92
01-01-2013, 03:04 PM #93
01-01-2013, 03:16 PM #94Professional Member
- Join Date
- Feb 2003
The York D1NA048N09006C gas pack breaks power to the R terminal when the limit, aux. limit, or rollout opens.
01-01-2013, 03:19 PM #95
I have already mentioned it once, if you don't want the stat to cut out during an open limit on that particular board, wire it to the red on the secondary side of the transformer on the primary side of the limits, there is no danger since the gas valve is protected by a high limit, jeeeezzz! how simple!
01-01-2013, 03:35 PM #96
01-01-2013, 04:36 PM #97
01-01-2013, 05:58 PM #98
01-01-2013, 08:08 PM #99
I don't make commission and make plenty of money of legitimate repairs during regular time.
Man, you are an extraordinarily frustrating person.
01-01-2013, 08:24 PM #100
01-01-2013, 08:57 PM #101
I tell people I power it off the unit to save them buying and replacing batteries. They like thatCol 3:23
questions asked, answers received, ignorance abated
01-01-2013, 09:01 PM #102
I normally just pull a new wire just so they can use the options
01-01-2013, 09:36 PM #103
For HVAC companies to stay in business and progress, they must build an annual customer base. Having a customer who you have installed a system for, but who did not see the value in buying an annual pm agreement, changing a t-stat battery is a very good way to keep that customer as a customer.
I am really sorry if my giving you sound advice for keeping customers frustrates you. May I suggest you just ignore me?Government is a disease......masquerading as its own cure…Ecclesiastes 10:2 NIV
01-01-2013, 09:39 PM #104Government is a disease......masquerading as its own cure…Ecclesiastes 10:2 NIV