Hello and thank you for allowing me to post on this forum.
About a month ago my furnace would not ignite due to a faulty "pilot light heat detector". I am sorry I do not have the technical name for this part. I replaced it and about a week ago my furnace is back to it's old tricks. Instead of the ignitor clicking continuously it only clicks once and stops. Therefore, the pilot light does not have to kick on and light the gas. I try shutting down the system and it works after I do it a bunch of times. When it does start to work it only stays on for about ten minutes and then shuts itself off again. The fan will still be running but no hot air is being pushed out. I played with the pilot gas adjustment and that seemed to work at the beginning but it no longer does the trick. Do any experts have any opinions on what the problem is and how to fix it?
I appreciate your help in advance.