I also forgot to mention that the Hum Stat lug on the board, it is designed to receive a signal from the thermostat, when it does call the two Hum terminals on the board, are what I call just a "dry contacts" they provide no power, they just close an on-board switch to complete the circuit for and optional de-humidifier or humidifier, the on-board relay will support 24 volts or 120 volts. Now how you can use those terminals to tweak the cfm's is way out of my league.
“Experience is a hard teacher because she gives the test first, the lesson afterwards". -Vernon Law-
"Never let success go to your head, and never let failure go to your heart". - Unknown
"To face tragedy is the greatest challenge; to overcome tragedy is the greatest success" -Ranal Currie-