Results 1 to 11 of 11
12-15-2012, 08:33 PM #1
would have set them a little different myself
Saw this downtown and had to snap a pic for you guys.
At least get that diffuser attachment.
12-16-2012, 11:59 AM #2
It's a 3 stage system...the guy on the end gets the short straw.....
12-16-2012, 12:13 PM #3
Yea I got a good laugh but seriously poor old unit on the end just got slightly overworked.
I foresee compressor failure in unit and new one sat exactly there......gees wonder what killed it?
12-16-2012, 12:37 PM #4
The compressor just "went bad". All that you need to know!!
12-16-2012, 12:53 PM #5
You mean my compressor ain't compressin'??
12-16-2012, 01:11 PM #6
I've changed 4 of them...it just keeps going bad. Junk compressors!!
12-16-2012, 02:52 PM #7
You see this is the torture test of modern a/c systems. All aboard the heat transfer trainwreck
1st unit control. Just 95deg at design oda.
2nd is simulating Arizona desert at 115 oda.
3rd is worst of all now condensing at 130!
12-16-2012, 03:58 PM #8
12-16-2012, 08:30 PM #9Professional Member
- Join Date
- Oct 2012
- La Crosse, WI
12-25-2012, 10:21 PM #10Professional Member*
- Join Date
- Oct 2009
- Raleigh, NC
There is a restaurant here that has three of them installed like that with barely 18 inches between them. On top of that they have surrounded all of them with wooden lattice.
12-26-2012, 05:22 PM #11