Results 1 to 7 of 7
12-14-2012, 06:12 PM #1
Honeywell XL15C Pump Lead Lag and Cooling Tower Control
In a week or so I have to program a XL15C for a rotating lead lag sequence for the pumps. I also have to set up a cooling tower staging control loop, and a boiler control loop. One of our Honeywell vendors gave me some example lead lag control loops for pumps. One of them has some logic loops, control loops, and math functions for a counter. I am assuming that this logic will rotate the pumps after a certain amount of time. The program he sent me was for a boiler system. So they created a control loop to enable the pumps below 60 degrees OAT. The output of this control loop is referenced in all of the logic loops for the pumps and counters. Being that my system was a cooling tower system. I was wanting pumps to run all of the time. If I deleted the pump control loop output from the logic. I am wondering if everything logic wise with the rotating lead lag would still work right?
I was also wondering if someone could explain how the whole integration time works on these control loops. What does increasing it do? What is this time based on? How can I know where to set this? Is there some type of formula that can be used to calculate this?
I have a copy of the program I was given if anyone wants to see it.
12-15-2012, 08:35 AM #2
Let me look at the program and I'll try and answer it, you should practice programming the 15c, there's a simulator avaliable online that will attach to the Lonspec software. As for integral, it's the funtion in the PID loop that allows the loop to stabalize before making another change to the output. The velocity model of the PID loop is the most popular but there are more out there, you have to look at the math to completely understand what's happening. In the volocity model the integral should be set as high as possible without causing erratic operation of the output, trial and error at first. Experience through practice will help you most.
12-16-2012, 07:42 AM #3
As far as the integral goes I have seen a lot of control loops on jobs without any integral. I am just trying to grasp the difference in all of the manufacturers integral setpoint. Some manufacturers use integral gain and it seems that this controller uses integral time. Will the simulator allow me to see the effect of this adjustment? Do you have a email I can send the program too?J. King
12-23-2012, 08:41 AM #4
I just put my email in my profile, I thought I had already put it there.
12-26-2012, 05:46 PM #5
12-27-2012, 08:37 AM #6
You were right I forgot the "2". If only I could type decently I would be a hellofagood programmer. Most of mu problems end up being typos.
01-07-2013, 08:17 PM #7J. King