Have to change oil on low pressure Chillers and have never done it before
Hey guys have I am a 5th year apprentice and given the job of changing the oil on 4 CVHF 700 tonners and 2 2550 CDHF dualees , have done the purge filters and and oil filters but not sure on how to do the oil , Im a visual person and reading the operation and maintenance manual dosent tell me very much besides do it though the oil charging valve , I know this is simple for you guys but I'm just looking for some direction so that I dont get air into the chiller.
Moderators, please move this thread to one of the chiller forums.
The key to happiness is lower expectations.
There are a couple of different ways to perform the maintenance procedure,
Get pro status and you may get the info You are looking for.
blast'em man blast'em
!!!KILL THE TERRORIST!!!
This isn't rocket science. Do you perform annual service on these chillers? How do you leak check them? That should give you one method. If you use hot water to heat the machines then you can get the oil out when the machine is under positive pressure.
Originally Posted by milkyway
Another method is an electric oil pump. Far easier and quicker than pressurizing the machine. Hook the suction side of the pump to the oil charging valve, start the pump and slowly open the charging valve. Make sure the discharge hose is secured in an empty bucket. Stop/repeat as necessary to get all the oil out. Make sure you don't turn off the pump before closing the charging valve.
Yep, that is what I was going to suggest.
Thanks for the info guys my 40 year chiller god just retired and the new chiller guy is unsure about Tranes and I wanna take the bull by the horns but dont wanna create more problems , we have heat packs on all the smaller chillers just never done a oil change before .Thanks KnewYork that makes sence to me, was always to busy else where in the plant to have my retired friend show me . I have done leak checks with the heat packs but I also read in some other post the some people dont like to use heat packs cause it causes pressures on the o-rings and creats its own leaks .
got his phone number? know where he lives? this forum is great and i love it, but there is a time delay to some answers and somethings are just easier said (over the phone, in person) than read.
Originally Posted by Troy Love
"Pimp My Service Truck"...that's a show I would watch!
Get me some rims and spinners, purple LED lights underneath, a disco ball and lasers....yeah!!! And make it a low rider!
Jayguy he retired and the only time I'm going to bother this friends is if I am knee deep .
And Troy, my comment about "rocket science" was not directed at you. It was directed at milkyway for suggesting you had to get to Pro status before something as simple as removing oil from a low pressure centrifugal could be shared. I won't go in to technical detail on this open forum, but am willing to share common knowledge items with anyone who asks.
What may be common knowledge to you may not be to others, the only reason I SUGGESTED to get pro status if one has never performed this they could be complications, example,.
1. Over pressurize / loss of charge
2. Accidentally interdiction of air
If u wanted to share you great knowledge/ then share it but no need to call anyone out for someone suggest to apply for pro status-
All I saw was a new guest status.
Thanks again Knew York going to attempt first oil change tonight
My first question to the OP would be why are you changing the oil in the first place ?
The toy chest is officially full ... I got a new toy..... 2007 Aston Martin V8 Vantage
You bend em" I"ll mend em" !!!!!!!
I"m not a service tech.. I"m a thermodynamic transfer analyst & strategic system sustainability specialist
In the garage , greasin', oilin' . tweakin' n shinin' Roll on spring 2015 !!