Should have one on everything. Also install a spill switch wired in series with the burner. Allow unit to run and get a hot flue. Then adjust draft to manufacturer specs. Check draft under the barometric or closest to the burner because this is the draft the barometric is controlling. most oil furnaces are set to -.02" w.c.