I went to the AHRI web site trying to extract some information and had difficulty finding it. I have a Carrier 24APA518A310 condenser that I want to use with a CNNP3014ALAAAAA coil. Knowing that the condenser is 1.5 ton and the coil is 2.5 ton, is it okay to move up 1 ton on the coil size? The TXV valve is EA36YD-106/R410A/3.00TR/TR6. The unit will be matched up with a Carrier 315AAV036070 furnace. Any thought on this match would be appreciated.