I like to have a positive 5-10 psig at the lowest pressure point in the system. This point is usually found at either the pump suction or at the highest elevation of the system. Check while in operation and at idle, just to be safe. This helps to ensure all coils are covered(or full) and no leaks suck air. OhioTech's formula is a great starting point, but verify with gauges.