Mini ductless best install practices
Mini Ductless units are a great source of entertainment and profits these days. This customer told me the unit worked just fine this summer, except that it was not working when he called. The unit had some strange wiring, which consisted of a four conductor cut just outside the piping exit wound in the building, the wire was spliced on two connections to a two conductor piece of romex which was again spliced to a piece of 18 gauge thermostat wire. Who knows what that was about, either way the communication wire to the indoor unit was installed onto the ground screw at the outside unit, and the ground wire was connected to the communication terminal.
Notice the number 10 wire running out separate hole in side of house and then up to the roof. No conduit needed, no insulation needed on the two lines behind the down spouting. If you cannot see the piping does it really need to be insulated, and does the hole need to be sealed shut?
While running a new wire, I removed the downspout (yes consistency) and found this great piping job. Sure this thing ran just fine all summer?
The customer said the guy made the holes with a hammer and chisel now that is cutting edge technology.
Lol oo wow. That's ridiculous and lazy.
Looks like he used his hammer and chisel as a bender too.....
Won't that require a new line set?
Which makes more sense to you?
- turning your thermostat back and being uncomfortable. Maybe saving 5-10%
- leaving your thermostat where everyone is comfortable. Saving 30-70%
DO THE NUMBERS! Step on a HOMESCALE.
What is comfort? Well, it AIN'T just TEMPERATURE!
Energy Obese? An audit is the next step - go to BPI.org
, or RESNET
, and find an auditor near you.
It may be possible to unkink with an adjustable wrench.... maybe not.... not much room and that kink is pretty sharp.
“I am for doing good to the poor, but...I think the best way of doing good to the poor, is not making them easy in poverty, but leading or driving them out of it. I observed...that the more public provisions were made for the poor, the less they provided for themselves, and of course became poorer. And, on the contrary, the less was done for them, the more they did for themselves, and became richer.”
― Benjamin Franklin
Originally Posted by ryan1088
i would throw up if that was exposed on the side of my house. wall of shame never ceases to amaze me