fan limit control
Just installed a thermo pride oil furnace ,what settings do you set up for the on and off on the fan control ,installed late last night ,going back to finish later in week ,heavy furnace, Thanks
The limits should already be set. What does the install manual say?
Shouldn't have to mess with it.
"The road to Hell is paved with progressive policies."
it was working.... played with it.... now its broke.... whats the going hourly rate for HVAC repair
140 on, 90 off upflow
Last edited by Kevin Weaver; 11-06-2012 at 03:21 PM.
Reason: added more
As iron sharpens iron so one man sharpens another Proverbs 27:17 NIV84
I would not set off any lower than 100° at the register or you most likely will get a call about it.
most likely it is already set, as has been said.
mfr should list limit, usually 200°.
on/off temps should be far enough apart to keep short cycling from occurring.
The Food Stamp Program, administered by the U.S. Department of Agriculture, is proud to be distributing the greatest amount of free meals and stamps EVER.
Meanwhile, the National Park Service, administered by the U.S. Department of the Interior, asks us to "Please Do Not Feed the Animals". Their stated reason for this policy "... the animals become dependent on handouts and will not learn to take care of themselves."
from an excerpt by Paul Jacob in Sun City, AZ
The limit temp. varies. It's in the manual. around 190. call me at Tech support if you have any problems with start up