Commercial Office Building Zoning question
I posted this in the controls area and didn't get any response, so hopefully you commercial gurus will have some ideas.
I have a customer that has purchased a commercial office building, the kind where you may find small offices for accountants and the like. Most of the rooms are maybe 12 x 12 with a few larger. Building is a rectangle in shape, laid out king of like ffices on front, hallway, offices in middle, hallway, and then offices on the back side of building.
So the hvac is (2) 4 ton heat pumps. One old Trane, one new Carrier. One does the front portion of the building , the other does the back side of the building, and for some reason they fed each of the center offices with a branch off of both units, which makes no sense to me. There are only 2 thermostats, and they are located in the hallways, which have no supplies or returns, so the thermostats are not measuring a realistic sample of the office temps.
The owner is wanting to add a system for one problem area, but I think he has enough air, it just isn't zoned or being sampled for temperature in a proper way.
So my first option to him is to place the thermostats in an office on their respective sides of the building to at least see what a room temperature is, instead of sensing an unsupplied hallway. Then ofcourse we have to ask which office.
My next option is to find a sensor type thermostat that will sense the return air temperatures (ceiling return, but this is the bottom floor of a two story building, so it should be a decent sample of the combined room temps) in hopes that a mixed sample of the room temps will find a median. And lastly we can add a zoning system, but it will have to cover 5 to 8 zones for each system. I will have to seperate the middle rooms to only be supplied by one unit and just zigzag the rooms. The supply duct is a straight sheet metal run, so if zoned each room will have to have a sensor and damper. The dump zone can be the hall way or the ceiling return plenum.
Anyway, I am hoping for some good suggestions and maybe a good brand of zoning system for an application like this. Hopefully the dampers can be mounted right on the 2x2 ceiling diffusers.
The main thing is to keep the main thing the main thing!
If "the grass is greener on the other side", it likely has been fertilized with Bull$hit!