i don't have an RAUJ wiring diagram, but it is probably similar to the RAUC.
the 1DL8 and 9 relays are time delays that will force the refrigerant circuit to stay energized for a minimum of 3 minutes once it has started.
you are correct on the 1K11 and 12 lockout relays.
step 3 (without any safeties tripped out) would be both compressors on Circuit #2 ON and Compressor 1A on Circuit #1 ON. Compressor 1B would not be running.
in SS-SVX11G-EN 01232012, page 113, it does say that Circuit #1 would be fully loaded and Compressor 2A would be ON. again, I don't have the wiring diagram to know if they have changed things since the RAUC manual. it could be a 'cut-n-paste' error...i would trust the wiring diagram more than the manual.
How to make the perfect "Half-Hitch" knot or any other boyscout knot in 3 easy steps...
1. Remove your meter leads from the meter and very carefully return them to their storage case or bag.
2. Wait 2 seconds
3. Very carefully remove your meter leads from their storage place and enjoy your new knot!