Not to distract from the OP, but to clear the air: I've done it numerous times on LON. Not that I recommend it, but it works. Even used dis-similar wiring on the same bus - 18/2 sheilded, non-sheilded, copper, copper tinned and even 22/2 echelon rated wire for the additions to the network. Worst case was around 50 nodes, had issues with a couple of devices dropping out, solved it with a LOYTEC device in smart switch mode which it filters out the junk and only passes the valid data. *From memory it was an L-Switch with 4 FT-10 ports and a 1250? port. Didn't use the 1250 port.
Originally Posted by control$
Last edited by crab master; 11-07-2012 at 06:44 PM.
"How it can be considered "Open" is beyond me. Calling it "voyeur-ed" would be more accurate." pka LeroyMac, SkyIsBlue, fka Freddy-B, Mongo, IndyBlue
BIG Government = More Dependents
"Any 'standard' would be great if it didn't get bastardised by corporate self interest." MatrixTransform