Results 14 to 20 of 20
11-01-2012, 10:53 AM #14
Some of the best techs on this board probably don't have formal schooling, but plenty of certifications and tons of experience that makes them some of the best in their field.
11-01-2012, 10:59 AM #15
The board may think that it's opened the gas valve, since it' throwing a no-flame fault. Menaing it thinks there should be a flame. IF it was a pressure switch, it woudl throw a code for pressure switch, thinking that the inducer had failed or there was low draft (obstruction).
See... you just have to think like a furnace. Its' easier ot troubleshoot a furnace for this reason, than troubleshoot a woman. A guy can think like a furnace... but sure as he** can't think like a woman. A furnace uses rational pre-programmed logic. A woman... well....
11-01-2012, 11:09 AM #16
There maybe an "on /off" switch on top of the gas valve. Is it on?
11-01-2012, 12:17 PM #17
11-01-2012, 03:46 PM #18
tim79, this is the Ask Our Pro's forum, and only Pro members that have been vetted by the AOPC may post advise here. Please apply to the AOPC today, thank you.
You can find the rules for posting and qualifications here.
Your post has been deleted.
Further infractions may result in loss of posting privileges.Contractor locator map
How many times must one fix something before it is fixed?
11-01-2012, 07:44 PM #19Professional Member*
- Join Date
- Dec 2002
- SouthEast NC ICW & Piedmont Foothills
11-01-2012, 08:50 PM #20Professional Member*
- Join Date
- Jul 2006