A visual inspection on a 90% furnace is difficult. Heat exchanger most likely have to be pulled. If the split is in the secondary heat exchanger a scope is useless. The pressure test with the magnehelic would be the best test, IMO, without pulling the heat exchanger. Typically a split on these units will cause the unit to shut down on pressure safety.