Results 1 to 13 of 51
Thread: High pressure trip w/ low charge
10-29-2012, 10:07 PM #1
High pressure trip w/ low charge
How is this possible on a 30RAP106. The IOM says it could!
This is what it says:
T126 Alert Circuit A High
Compressor operation outside
of operating envelope. Circuit shut down
Automatic, only after
first 3 daily occurrences.
Manual reset thereafter.
Reading from OAT
sensor must drop 5 F
(2.8 C) before restart
And these are the possible causes:
Faulty transducer, low/
airflow, low refrigerant charge,