Found a circuit flat on charge yesterday and repaired it today.
found leak at 50psi nitrogen and bubbles to verify
better picture of whole coil
repaired leak with #0 tip
also found this fitting to leak and replaced
the coil all back together
not a bad level for r-410a thats been open to atmosphere for who knows how long
i also replaced the drier with a correct size one.