Results 14 to 15 of 15
Thread: reach in freezer help needed
10-18-2012, 07:57 AM #14
When you relocated the condensing unit, how long was the system open?
10-18-2012, 09:29 AM #15
Is the DTS working? Your CPR may be toast but it may be only a symptom. If DTS is stuck and not terminating defrost on temp the htrs will stay on till temp limit trips making for a hot evap then when timer times out the fans will come on. Hot evap+fans=super load. CPR may just be screaming for help. Just a thought.