Im working on a cgafc air cooled chiller used for process cooling, my problem is the unit keeps shuting off on HI comm loss between modules, unit says check wiring, all looks good even the connections, i will add that the last time i had this happen i changed the (1u something number board,cant remember number) and all was well for a while,I changed that board due to corrosion,should have cahnged the others next to it as well(1u90 and 1u91) but trying to save money, anyways when i shut power off and reapply it, unit says HI comm loss check wiring between modules. I have several other units i have to work on so this one is on the back burner, any info is appreciated
the wires are not shielded so look for ANY wires that carry ANY voltage and move them far away.
When she gets lonely and the longing gets too much
She sends a cable coming in from above
Don't need a phone at all
We got a thing that called radar love
We got a wave in the air...radar love....Golden Earring