Results 1 to 3 of 3
Thread: Trane RTU thermostat
10-08-2012, 04:38 PM #1
Trane RTU thermostat
I have a customer with a Trane RTU model YCD180B3H0AA, 1991 UNIT. Currently has a BAYSENS008B Thermostat.
They want a programmable but the Trane Customer service said " They don't make one for this".. REALLY?
I know this is a sensor type stat and isn't conventional, but surely I can get one.
Any help appreciated!As iron sharpens iron so one man sharpens another Proverbs 27:17 NIV84
10-08-2012, 06:23 PM #2
How about a conventional thermostat interface board in the RTU so you can use any appropriate 24v stat? Seems to me that's how they did things back then.
10-08-2012, 06:36 PM #3Professional Member
- Join Date
- Feb 2012
BAYSENS019B/020B is a programmable one and you do not need a CTI board for it to work.