Originally Posted by 2sac
What about the chance of copper shavings getting into the system and causing another restriction?
I said drill, but what I would really do is pop a small hole in the suction with my torch
FSE_ that's a weird couple of posts. Have you done either of those things with the drill or torch before
If You Can Dodge A Wrench You Can Dodge A Ball
I think an ice pick shoved thru the copper would be best , then shove cap tube into it
On the condenser end , cut the suction pipe in half , drill a hole through a coupler , pull cap tube thru pipe , shove through hole in coupler , put coupler in place.
All theory and sounds easy of course on paper ....