10 Ton Trane Pkg Gas Rooftop Install 208/230 V 3Phase
Is that green wire a ground ?
Sent from my SCH-I800 using Tapatalk 2
Looks like the line side wiring is undersized, in the pic it appears to be 10ga wire. Should have been at least 6ga wire going to that terminal block.
When you do a job, Always make it easier for the next guy, because you may be the next guy working on it.
It is at least a 6 may be a 4.
That's what they call a single phase conversion. Attach the green wire to the terminal block and it becomes 3 phase.
Local 597 Service Fitter
Metal Trade Journeyman
PAY ME NOW OR PAY ME LATER
It was working when I left...
Liberalism-Ideas so good they mandate them
There's a mess in the bottom left of the screen I cant make heads or tails of and it looks like one or more wires have the insulation tucked under the screw.
its 208 volts and the tap on the transformer is at 230
i was also seeing the insulation under the screw
Not sure if the middle leg got pushed in all the way. And why are there jelly fish swimming just below the terminal block?
Common sense isn't very common anymore.
Got a little warm at one point, did it?
Please excuse me if my post looks like it was typed by a teenager. It was sent from my phone.
I do three kinds of work.
1 - Good - 2 - Fast - 3 - Cheap
Electricity does not care what color the wire is.
Whatever that is below to the left... heated and caused the supply wires insulation to cook?
Galatians 2:20-21; Colossians 1: 21-22 & 26-27; 3:1-4; Romans Ch's 5-6-7-8
2 Chronicles 7:14
Quality work at a fair price with excellent customer service.