You're good to go.
you only need an externally equalized valve if you have a pressure drop greater than a 2º SST drop across the evaporators.
Which would be caused by a large evaporator or a distributor nozzle.
Results 14 to 16 of 16
Thread: TXV for Trualsen reach in cooler
Used Equipment - Buy, Sell, Save!